Switches | Outlets & Plugs | Ballasts | Replace Ballasts | Troubleshooting | Light Bulbs | Basic Electricity | Save Energy | Misc Articles
With conventional dimmer wiring using NM cable, a NM cable supplies 120 volts from the electrical panel to the dimmer outlet box.
Another NM cable connects from this dimmer box to the light fixture box. Both 120 volts and neutral travel from the switch box to the light fixture box.
Diagrams shown on this page are simplified for clarity. Electrical outlet boxes can have numerous NM cables going in and out. See Actual Switch Box Wiring.
Ground connection diagram is shown separately.
Typical 3-way Dimmer Wiring Diagram
Conventional Dimmer Wiring Diagram
In the diagram below, a 2-wire NM cable supplies power from the panel to the dimmer box. The black (line/hot) wire connects to the common terminal of the 3-way dimmer.
A 3-wire NM connects the travelers of the dimmer to the travelers of the 3-way switch. Traveler wires are interchangeable on each switch. The 3-way dimmer and 3-way switch are also interchangeable.
The common terminal of the 3-way switch connects to the light fixture(s).
The white neutral wires are connected together in each switch box.
Light Switch Wiring
Multiple Switch Wiring
3-way Switch Wiring
Alternate 3-way Switch Wiring
4-way Switch Wiring
Alternate 4-way Switch Wiring
Dimmer Switch Wiring
Photocells and Timers
Ceiling Fan Switch Wiring
Motion Detectors and Occupancy Sensors